mailing list archives
Re: Re: telehouse - 25 broadway
From: mike harrison <meuon () highertech net>
Date: Sun, 16 Sep 2001 17:58:26 -0400 (EDT)
How many folks actually perform a load transfer to the generator during
testing to check out the transfer switch ?
Back in my military hospital days, we did both regular load tests,
using a LARGE resistive loads we flowed water through to cool (4" feed
pipe) as well did actual swapovers (on weekends).
Never seen it done that way since, when we bought our current generator
system the company that installed it thought I was crazy for even asking
about a test load.
We do do a full swapover every few months... --Mike--
Re: Re: telehouse - 25 broadway David Lesher (Sep 16)
- Re: telehouse - 25 broadway, (continued)