mailing list archives
DoS vulnerability in Siemens S7-1200 PLCs
From: Arne Vidström <arne.vidstrom () foi se>
Date: Thu, 20 Dec 2012 17:07:13 +0100
I have found a DoS vulnerability in the Siemens S7-1200 PLCs. It is present in firmware versions 2 and 3. After an
exchange of specially crafted packets to TCP port 102 the PLC shuts down. The red, green and yellow status LEDs start
flashing. All outputs are shut off. The device stops listening at port 102 and becomes completely non-responsive.
Sometimes a few status messages are sent before it shuts down. They state that a serious firmware error has occurred
and that the PLC is defective. Power cycling the PLC restores operation though.
More information can be found in the Siemens advisory:
Best regards /Arne
Swedish Defence Research Agency (FOI)
- DoS vulnerability in Siemens S7-1200 PLCs Arne Vidström (Dec 24)